Photo 1: Valiant 120KW Commercial Boiler
Installed in the preformed Boiler Plant Room, by our Gas Safe Engineers February 2019. Note: Isolation Valves are fitted throughout the plant room for ease of Maintenance.
Photo 2: Pressurised Cylinder.
Installed in the preformed Boiler Plant Room, by our Gas Safe Engineers, with pressure safety controls installed
Photo 3: Four Zoned Heating System.
We designed the Building Heating system into 4 Zones, each with their own Thermostat, and control Valve. Isolation Valves are fitted either side of each Zone Valve, to save having to drain the whole system to replace or repair when they fail to work after years of constant ware.
Photo 4: Expansion Vessel.
This was calculated to give the correct Expansion space required if all 4 Zones were working at Maximum Temperature and the Hot Water was also demanding Heat.
Photo 5: Dosing Pot. & Automatic Filling Vessel.
Dosing Pot Installed to facilitate the addition of cleaning fluid during the initial testing, and removed after 2 Days to add Inhibitor.
The Automatic Filling Vessel was installed to save having to top up the system, when the loss of pressure with natural expansion of the Heating System occurs.